The disinfection of water plants has been developed for many years, but the word "chlorine" is still inseparable! This is because it is required in the national system standard that there must be chlorine disinfectant in drinking water to control the reproduction of microorganisms.
As we all know, in the production process of drinking water, the purification and disinfection process is the key process to ensure the safety of drinking water, and the disinfection process is the most important. At present, the commonly used disinfection methods include sodium hypochlorite disinfection, chlorine dioxide disinfection, chlorine gas disinfection, etc. Among them, sodium hypochlorite disinfection, as a broad-spectrum, efficient and safe disinfection method, has become the mainstream disinfection method for drinking water, but the process involves the detection of parameters. It's a headache for the inspectors!
To this end, in order to save you worry and effort, we have tailor-made sodium hypochlorite disinfection testing solutions for you. It is suitable for water plants disinfected with sodium hypochlorite generators or finished sodium hypochlorites. Comprehensive planning of disinfection testing and evaluation, disinfection from the source The control of the agent involves the monitoring of the disinfection effect in the process, and then to the evaluation of the disinfection effect of the factory water and pipe network water, and realizes the whole process monitoring of the tap water disinfection.
Recommendations for storage and use of sodium hypochlorite
1.During the storage and use of sodium hypochlorite, the water plant should strengthen the monitoring of the effective chlorine concentration and chlorate by-products, and determine the appropriate storage time according to the local climatic conditions and the production situation of the water plant. The temperature is always higher. In regions, it is recommended to use air-conditioning and other temperature control measures to reduce the storage temperature in summer, and try to control the room temperature below 25 ℃.
2. Before filling the medicine storage tank (pool) with new medicine, try to use up the medicine in the medicine storage tank (pool), and regularly empty and clean the medicine storage tank (pool) to minimize residual liquid .
Post time: Nov-25-2021